Water contains three major impurities physical, biological, chemical. Physical impurities troubles in various industrial, commercial and domestic applications hence for better quality physical impurities required to reduce up to application standards. We manufacture and supply range of MGF Filter. Physical impurity is decreased by filtration, various kind of filtration system available for different application with different sharpness of removal in macro to micron. pipes of polyvinyl chloride (PVC) and all the filters have a single multi-port plastic valve operated by a hand lever except the smallest ones where plastic ball valves are used. we use it for control of drip and sprinkler irrigation system for field water softining applications.Specially designed for a variety of water control applications, DSF series valves are made out of sturdy, durable, corrosion resistant, high-quality materials, and produced by our ISO accredited factory.
Softening is the ion exchange process, it is done through resin, the most common and probably the easiest method of removing hardness (that is calcium and magnesium) from water and suitable for utility purpose. As the name implies ion exchange is a process in which undesirable ions are exchanged for more desirable ions. The softening process consists of passing raw water containing hardness through a bed of cation resin in sodium form. The hardness ions Ca & Mg are taken up by resin and in exchange, the sodium ions are relinquished from the resin. This is called the service cycle, where the hard water is being softened. CHEMICAL REACTION DURING SOFTENING PROCESS :- Ca (HCO3)2 + Na2 R = RCa + NaHCO3 CaSO4 + Na2 R = RCa + Na2SO4MgCl2 + Na2 R = RMg + NaCl REGENERATION PROCESS :- Raw water will continue to get softened till the resin gets exhausted. Bringing back the resin to it original form is called regeneration. Softener resin is regenerated by sodium chloride- Nacl (Common salt) solution. The common salt solution is kept in the regeneration tank. During the regeneration process, salt solution is injected by the ejector tube into softener. The Nacl (salt solution) replaces ca, Mg (Hardness) from the resin, the regeneration is done every day or every few days or every week depending upon the usage and design of the water softener plant.